The current loop technology for serial data communications is a technique that has some advantages over the more widely used voltage approach.
Driven from a constant current supply, current loop is able to provide communications over long distances where voltage drops might be an issue.
Although a variety of current levels can be sued, the most common, by far is 20 mA current loop.
The 20 mA current loop scheme is has been used for many years for sending digital data. Although not a formal standard, it is a de-facto standard that that was widely used for many serial data communications applications. It was been incorporated into the old teleprinters or teletypes for sending data between two equipments along with being used in a variety of other applications. In fact many older machines (prior to the 1960s) used a 60 mA current loop system, although later machines adopted a 20mA current loop standard - the first one being the Model 33 teletype.
Nowadays the current loop system is not as widely used, but it still finds applications in a number of areas resulting from its advantages. When RS-422 was first introduced (first introduced in 1978) and then RS-485 (first introduced in 1983), the popularity of 20mA current loop soon waned. It is now seldom used, but included here for completeness.
Advantages and disadvantages of current loop
The 20mA current loop format for serial data communications has a number of advantages that mean it is still used in a variety of applications. However it is necessary to balance the advantages and disadvantages for any application.
20mA current loop advantages
- Line losses are not usually significant: The fact that a current source is used means that voltage losses caused by line resistance are unlikely to cause a problem.
- Can be used for long distances: As voltage losses are not normally significant, 20mA current loop systems can be sued for carrying data over long distances, sometimes up to several kilometres.
- Can be isolated from ground: By using opto-isolators it is possible to isolate the signalling system from ground.
- Provided a simple form of networking: As the system uses a current loop, it is possible to run several teleprinters receiving data from one source by placing each teleprinter in the loop. This meant that 20 mA current loop provided an early form of networking.
20mA current loop disadvantages
- No official standard: No recognised standards bodies have ever published a standard for the 20mA current loop system. This has meant that there are areas of uncertainty. For example it is necessary to know some technical details of the interface circuits to ensure that they interface correctly.
- Slow speed: The speed at which current loop systems are able to transmit data is generally much less than voltage based systems. However for short distances speeds up to 19.2k baud are possible, although for longer distances it will be necessary tor educe the speed, possibly as low as 300 baud.
- Convenience: The circuits used for voltage based signalling systems are generally more convenient than those used for 20mA current loop.
- Signalling: Many voltage based systems use multiple lines for handshaking which speeds the operation. 20 mA current loop traditionally only uses two lines and therefore any handshaking signals need to be carried within the messaging making it less flexible.
Analogue current loop
While the current loop system described here focuses on a digital format used for data signalling, other systems use an analogue approach. These schemes generally use a 4 - 20 mA current loop system and can be used to control transducers.
Although a little crude by today's standards, analogue 4-20mA current loop systems allow control over a single pair of wires and again the resistive losses are less significant, enabling more accurate control than that provided by a voltage based system over a distance.
Additionally, analogue systems such as this current loop system are easier to troubleshoot that any digital systems that could be used. However they may be much less flexible as only one parameter can be controlled at any one time.
While the 20mA current loop system is not as widely used as it used to be, it is still found in some niche areas. It still has advantages to offer in terms of distances that can be covered and the noise immunity it can offer. However it was never adopted as a formal standard and this means that when using equipment with 20mA current loop, it is necessary to check the specifications of the interfaces of both transmitter and receiver.
Wireless & Wired Connectivity Topics:
Mobile Communications basics 2G GSM 3G UMTS 4G LTE 5G WiFi IEEE 802.15.4 DECT cordless phones NFC- Near Field Communication Networking fundamentals What is the Cloud Ethernet Serial data USB SigFox LoRa VoIP SDN NFV SD-WAN
Return to Wireless & Wired Connectivity